[ List Subjects ][ Post Message ]
Subject: Re: Variable pressure operation
[ View Followups ][ Post Followup ]
Date: 09/24/00 at 11:07 PM
Posted by: Fred Pfeifer
In Reply to: Re: Variable pressure operation posted by Anthony Salvarezza on 05/11/00 at 10:10 AM:
The heat rate savings for a drum type unit are primarily due to reduced pumping power. If electric boiler feed pumps are used, this is wasted due to throttle losses in the drum level regulator. If a variable speed feedpump is used, some savings will be realized. I have found that the primary benefit if variable pressure operation is the reduced turbine stress since the first stage inlet temperature is constant.
Post a Follow-up: