[ Post a Follow-up ][ New Thread ]
Subject: Tapping of sourse
Posted by: Francis Foo
E-mail: foo4008j(at)singnet(dot)com(dot)sg(no spam)
I intent to tap supply from a socket outlet or lighting source,
connecting to a small distribution box
(of course the rating must be lesser than
the origin MCB), but how to connect in the way that went the "down stream" is
having over load or earth fault, it will not infringe the main origin
distribution box ?? Can the type 3 switch gear do the job???
Please enlighten me, if possible with simple circuit diagram.
Post a Follow-up:
This message has been here for a period of time, a follow-up seems
unnecessary. In this place we have stopped the functions of [post a
follow-up]. To discuss and communicate your ideas/info, you may use our
new message boards, please go to: Electrical
and Electronic Community
When you do want to contact the author of this message, you must
replace the "(at)" with "@" and "(dot)" with "." in his/her e-mail
address above. But, please do not spam...
To create a new thread, please go to the current board of discussion forums.
On that page, click the [Post a Message] or [New Thread] link, then you will find
the submit form.
There are more than 55 boards in our site. Please choose, according to your topics,
an appropriate one to post your message. If you are new comers, we suggest you to go
to our Homepage to have a clear knowledge of the subjects and the orientations of
our site before you post any messages.